Opretholdelse af et røgfrit område skaber en flugtvej og bedre adgang for brandfolk.
10 etagers bygning
For space-constrained multi-storey residences requiring mechanical smoke extraction to maintain smoke-free means of escape and fire fighter access. Mechanical smoke extract from corridors/lobbies provide reduced riser areas, can provide increased travel distances and is less susceptible to adverse wind pressures acting on the discharge Air Operating Vent [AOV] when compared to natural smoke vent systems.
1No. SMHA extract fan was selected to provide the required extract duty, 20No. ESAS smoke control dampers – one per level on extract side and 1 per level on make-up air route were provided to allow for only the fire level to have smoke ventilation, all other levels were closed off to prevent the spread of smoke. CFD analysis was also provided for this project to demonstrate the visibility achieved.
10 storey apartment building with a calculated fire load of 1MW in a residence with door held ajar by debris during occupant escape, causing smoke spread into the connecting lobby with other residences and an extended travel distance to the single escape stair core.
Ventilation requirement: smoke extract from corridor to increase visibility for fire-fighter access.
Ved at bruge denne hjemmeside accepterer du vores brug af cookies. Cookies er små tekstfiler, der gemmes på din computer. Dette giver os mulighed for at forbedre din browseroplevelse og gør det muligt for os at forstå, hvordan du bruger vores websted. Flere detaljer kan findes på vores 'Vilkår for brug' side.